More examples & information related to Aerial Electrical can be found here:
Buss Bar Fabrications
These are examples of our trade-persons view
of what normally goes unnoticed with electrical over-heating in various circumstances.
Burnt Internal HID
Lamp Socket and
Broken porcelain lamp socket. Causes shorten lamp life. This is
sometime caused by poles having too much wind-blown movement.
Burnt wiring inside a
circuit breaker panel.
Burnt wires in buried
Burnt wiring in-ground
Pylon Sign with totally burnt out internal components.
Burnt electrical wiring due to damp conditions in areas rarely seen.
Burnt wires, electrical fire inside a large wiring splice box due to continued water entry.
Burnt and broken wiring circuits due to deterioration inside crawl space.
Burnt electrical connection for neon glass tube.
Burnt electrical panel Buss-Bar where the circuit breaker grips on to the power distribution point.
Burnt electrical receptacle from ice build up inside the outlet box. This is
slow burn and is difficult to detect because it does not show on the outside.
Parking Area Security Lighting.